Maximum cooling capacity
Optimal water consumption for 10 kW
5x50-70 mm² (copper conductors)
3/4-1 inch (for tap water)
Power consumption per pump
Assembled weight (without coolant)
Dimensions with lid (LxWxH)
Detailed description and instructions
The stock unit is designed for heat removal of 324 MJ or 90 kW/h of electricity. For example, 18 Antminers S19 x 5 kW (max. el. power overclocked) = 90 kW/h. The unit itself consumes 0.345 kW for the work of circulator pump. Installed heat exchanger should be connected to a source of cold water below 20 degrees Celsius. Tap water can be used as well as water from a well, a reservoir (river, pond, lake) or a closed circuit (pipes laid in the ground, floor heating, heating of water intake, etc.).
Electrical connection. The unit connects with a 50-70 mm² x 5 copper core cable. In the local distribution board the cable should be protected by a 200 amps automatic circuit-breaker and RCD, or a 200 amps differential circuit-breaker. In the unit's board the cable is connected to an initiatory 200 amps circuit breaker, which is followed by contactors that switch power for miner's circuit-breakers (18 circuit breakers in total, 1 per each miner). The board also features circuit breakers for control chain, pump, ethernet switch and an additional socket for connecting computer, etc. There are also temperature and voltage relays in the board.
Water connection. The unit connects with any water-supply pipe including flexible flow pipe. A 1" flexible flow pipe is enough to connect to a main water supply. In other cases we will consult you if needed. The water-supply pipe should be connected to the lover nozzle, so that water in the heat exchanger would move in the opposite direction from the coolant. It is advisable to put a mesh filter for primary water refining and a valve for smooth adjustment of water flow to the heat exchanger. Volume of cold water supplied determines temperature of the coolant in the unit. Recommended coolant temperature is 35-40 degrees Celsius (for Antminer S19 overclocked, may vary for different miners).
The unit comes equipped with overheat protection. The thermostat is set to 48-52 degrees Celcius. When the unit heats up to 52 degrees it shuts down. After cooling down to 48 degrees it will turn on automatically. The user is able to change values of those thresholds, however it is not advised to set them above 60 degrees. The unit also features a system that automatically turns it off when level of coolant in the tank is lower than critical. The developer maintains the right to perform changes in the construction for the sake of it's improvement.
Contact us if you need delivery beyond Russian Federation.